QF2 Fire Protection Compound may be used in all types of building and is compatible with most building materials. QF2 Firestop Compound is simply added to clean water either in a bucket or a concrete mixer, mixed and poured or trowelled into position.
The setting time for QF2 Firestopping Compound depends on the atmospheric temperature. It may be built up further within two or three hours where large barriers are required. Do not attempt to use a mix ratio of less than 2:1 mortar to water volume. Adding further water to the partially cured system must be avoided at all times as this will irreversibly interfere with the curing process.
For horizontal barriers it is recommended that MW Mineral Wool Shuttering Slabs are tightly fitted into the opening so that the QF2 Mortar may be poured on top of the slab to the required thickness. It is recommended that the mineral wool slab is not removed but remains in position as this offers an enhanced period of fire resistance.
Where the barrier is required to provide a load bearing capability consideration should be given to structural support, such as reinforcing bars. Consideration may also be given to the use of a permanent shuttering system. In all loadbearing situations mortar thickness must be at least 100mm.
Where the thickness of the seal is built up using multi layers, the structural strength of the seal may be reduced. It is therefore recommended particularly in load bearing situations that a maximum of 10% thickness is installed initially and the remaining thickness applied as a further single operation.
For vertical or wall barriers it is recommended that MW Mineral Wool Shuttering Slabs is installed as a tight fit into the aperture at the centre line of the fire compartment wall. QF2 Fire Protection Compound may then be ‘plastered’ to a minimum thickness of 25mm to each side of the slab.
All gaps surrounding cables, ducts or pipework penetrating fire compartment floors or walls to be filled with QF2 Fire Protection Compound to a minimum depth of 50mm. Combustible services must be fitted with a suitable fire stop seal such as a QWW CE Marked Intuwrap or QWR CE Marked Fire Collar.
For installation in floors MW Mineral Wool Shuttering Slabs can be installed friction fitted around penetrating services as a shutter. QF2 Fire Protection Compound should be applied over the MW Mineral Wool Shuttering Slab to a minimum thickness of 50mm.
For installation in walls MW Mineral Wool Shuttering Slab can be installed friction fitted around penetrating services. QF2 Fire Protection Compound should be applied to a minimum thickness of 25mm on each side of the MW Slab.
For a loadbearing seal the QF2 Fire Protection Compound must be applied to a minimum depth of 100mm.