Quelfire QWW CE Marked Intuwraps prevent the spread of fire through PVC, HDPE & PP pipes where they penetrate fire compartment floors.
Next Day Delivery
Fast response to all enquiries
40 years of experience
• Tested to BSEN 1366-3: 2009
• CE Marked
• Up to 4 hour fire rating
• Suitable for PVC, PVC-U, PE, HDPE, MDPE, PP & ABS pipes
• Available for 32—160mm pipes
• Can be retrofitted
• No mechanical fixings required
• Performance unaffected by weathering (Type X Durability)
Building Regulations impose limitations on all pipes passing through fire compartment floors. Quelfire QWW CE Marked Intuwraps allow plastic pipes to meet the requirements of the Building Regulations. Quelfire QWW CE Marked Intuwraps have been tested according to BSEN 1366-3: 2009 where pipe diameters of up to 160mm have met insulation and integrity criteria for this standard for up to four hours.
The Quelfire QWW CE Marked Intuwraps consist of a high performance graphite based intumescent material within a polythene cover which reacts under the influence of heat to exert pressure on the pipe as it softens to form a carbonaceous char which provides an effective insulation plug thus preventing smoke and fire passing through to the adjoining compartment. The QWW CE Marked Intuwraps have a self-adhesive tab which secures the wrap around the pipe.
Tested to Type X durability which means the QWW CE Marked Intuwraps can be installed in conditions exposed to weathering. Quelfire QWW CE Marked Intuwraps are expected to last the lifetime of the building.
Quelfire QWW CE Marked Intuwrap should be placed around the plastic pipe and secured using the built in self-adhesive tab, with the lower edge of the Intuwrap level with the soffit of the floor. It is essential that there is no gap between the surrounding constructions. Any gaps should be grouted using the Quelfire QF2 Fire Protection Compound.
Should you require any further information regarding this product, please don’t hesitate to contact one of our specialists.
|Product Code||Pipe Size (mm)||Space needed around pipe to fit QWW (mm)||Recommended hole diameter (mm)||QWW Length (mm)||Fire Rating|
|QWW32/CE||32Ø||4||42Ø||60||Up to 4 Hours|
|QWW40/CE||40Ø||4||50Ø||60||Up to 4 Hours|
|QWW50/CE||50Ø||4||60Ø||60||Up to 4 Hours|
|QWW55/CE||55Ø||8||73Ø||60||Up to 4 Hours|
|QWW63/CE||63Ø||8||81Ø||60||Up to 4 Hours|
|QWW75/CE||75Ø||8||93Ø||60||Up to 4 Hours|
|QWW82/CE||82Ø||8||100Ø||60||Up to 4 Hours|
|QWW90/CE||90Ø||8||108Ø||60||Up to 4 Hours|
|QWW110/CE||110Ø||9.5||132Ø||60||Up to 4 Hours|
|QWW125/CE||125Ø||13.5||155Ø||60||Up to 4 Hours|
|QWW160/CE||160Ø||19||200Ø||60||Up to 4 Hours|