Quelfire GM Intumescent Acoustic Acrylic Sealant is a halogen free, polymer emulsion based sealant that swells when subjected to temperatures in excess of 125oC and forms a char coat that restricts the passage of smoke and fire. It is easily applied and dries to a flexible and smooth surfaced material which is readily over paintable. It has excellent adhesion to a wide range of substrates and will not harden or crack with age. It is suitable for perimeter pointing around services, and for use in low movement linear joints in walls and floors.
Next Day Delivery
Fast response to all enquiries
40 years of experience
• Tested to BS EN 1366-3: 2004 & BS EN 1366-4: 2006 & BS 476: Part 20: 1987
• Up to 4 hour fire rating
• Tested to BS EN ISO 140-3
• Up to 55dB sound reduction
Building Regulations impose limitations on all gap and joints Quelfire GM Intumescent Acoustic Acrylic Sealant has been tested to BS EN 1366-3: 2004 & BS EN 1366-4: 2006 achieving 4 hour integrity and insulation rating for a range of linear and penetration seals.
Quelfire GM Intumescent Acoustic Acrylic Sealant is a halogen free, polymer emulsion based sealant that swells when subjected to temperatures in excess of 125oC and forms a char coat that restricts the passage of smoke and fire.
Quelfire GM Intumescent Acoustic Acrylic Sealant is expected to last the lifetime of the building.
Surfaces to be sealed must be clean, dry and free from dust, dirt, frost, grease and other contamination. Cut both the cartridge tip and applicator nozzle to the required diameter and angle, screw nozzle onto cartridge. Apply sealant with applicator gun ensuring good surface contact is achieved by forcing sealant into the joint to be sealed. If necessary, tool within 5 minutes of application using a spatula dipped in soapy water, apply sufficient pressure to ensure good contact of the sealant against the joint surfaces. Ensure that a depth of mastic of at least 20mm can be achieved. Gaps deeper than this may be back-filled with conventional foam material or mineral wool as required. For gaps not more than 10mm width a 10mm depth of mastic is sufficient.
When installing Quelfire SS System, the Quelfire GM Intumescent Acoustic Acrylic Sealant should be used to seal around the services and the edges of the SS System ablative coated fire batt.
One 310ml cartridge contains sufficient material to seal approximately 4 metres of a 12mm x 6mm joint.
Should you require any further information regarding this product, please don’t hesitate to contact one of our specialists.